1.15.1. Switches of a heating system and ventilation
|Switches of a heating system and ventilation are located on the average console. Are their part:
– the lever (9) moved in the horizontal plane operating intake of air;
– three round handles for management of an operating mode of the fan (6), temperature (7), distribution of air (8).
Management of intake of air (9)
The lever in the left situation
The lever in the right situation
Management of distribution of air (8)
Turning the handle counterclockwise, it is possible to find the following four provisions:
Management of air temperature (7)
Mark in the handle in the left extreme situation opposite to a blue hyphen: switching off.
Turn of the handle clockwise: gradual increase in intensity of heating.
Mark in the handle in the right extreme situation: maximum intensity of heating.
Control of the fan (6)
Mark in the handle in extreme situation after turn counterclockwise: switching off.
Turn of the handle clockwise: gradual increase in amount of the given air.
SIDE AND AVERAGE NOZZLES OF VENTILATION
On both sides of the forward panel there are two exhaust outlets for air closed by special lattices which allow to establish and regulate the direction of a stream of air.
Special exhaust outlets direct air to glasses when the handle of distribution of air (8) is in situation